Compact Recessed Passive Infrared Dimming Occupancy Detector
The ASENS-CPIR-PRO is a passive infrared occupancy detector ideally suited to controlling all types of switchable lighting. When movement is detected, the luminaires are switched on. When an area is no longer occupied, the luminaires will switch off after an adjustable period of time. The detector can be changed from presence to absence detection by using the external switch or the ASENS-CHSLCD.
The internal light sensor provides additional energy saving potential by integrating photocell holdoff. When an area is occupied, the lighting is only switched on when the level of natural light falls below a preset level.
The ASENS-CPIR-PRO has a two channel capability for use with both digital dimming and switched lighting loads. For example, in a classroom, the window row of luminaires can be dimmed down according to daylight detection and the rest of the luminaires are switched on and off only. Two input terminals can be used to manually override the dimming levels and override the luminaires on and off.
- Basic Programming Handset
- Advanced LCD Programming Handset
- Surface Mounting Box for DDC311, DDC313, ASENS-CPIR and ASENS-C6MW
- Avoid direct sunlight entering the detector
- Do not install within 1m of forced air heating or ventilation
- Do not install within 1m of any lighting
- Do not fix to a vibrating surface
|Supply Voltage||230V AC 50Hz|
|Channel 1 Load||10A fluorescent, low voltage, LED|
|Channel 2 Load||Maximum number of digital dimming ballasts = 10 (relay enabled)|
Maximum number of digital dimming ballasts = 20 (relay disable)
Dimming output is not SELV, Mains rated cabling must be used.
|Power Consumption||On = 625mW|
Off = 807mW
|Timeout||Adjustable 10sec to 30min|
|Light Level||Light to Dark|
|Material||Flame Retardant ABS Type 2|
|Temperature||-10°C to 35°C|
|Humidity||5% to 95% non-condensing|
|Compliance and Standards||EMC-2004/108/EC|
Wiring Diagram 1 : Switch And Dim Together
Switches the luminaires with occupancy and maintains illuminance, Dims and switches using the optional centre biased retractive switch.
Wiring Diagram 2 : Switch An Dim Separately
Switches both channels with occupancy, maintains illuminance, dims and switches the dimming channel using the optional switch 2. Switches the switching channel using the optional single position retractive switch 1.
Wiring Diagram 3 : Two Channel, Common Switch
Switches both channels with occpuancy. Maintains Illuminance, dims and switches the dimming channel using optional centre biased retractive switch.
Wiring Diagram 4 - Single Switch Only
Switches channel 1 only with occupancy, optional override switch. No dimming output.