Recessed Microwave Dimming Occupancy Detector
The ASENS-C6MW-PRO is a recess mounted microwave occupancy detector ideally suited to controlling all types of switchable lighting. When movement is detected, the luminaires are switched on. When an area is no longer occupied, the luminaires will switch off after an adjustable period of time. The detector can be changed from presence to absence detection by using the external switch, the ASENS-CHS5 or the ASENS-CHSLCD.
The internal light sensor provides additional energy saving potential by integrating photocell holdoff. When an area is occupied, lighting is only switched on when the level of natural light falls below a preset level.
The ASENS-C6MW-PRO has two channel capability for use with both digital dimming and switched lighting loads. For example, in a classroom, the window row of luminaires can be dimmed down according to daylight detection and the rest of the luminaires are switched on and off only. Two input terminals can be used to manually override the dimming levels and override the luminaires on and off.
The functionality of the ASENS-C6MW-PRO is controlled by a number of parameters which can be accessed using an infrared remote control such as the ASENS-CHSLCD.
- Basic Programming Handset
- Advanced LCD Programming Handset
- Surface Mounting Box for DDC311, DDC313, ASENS-CPIR and ASENS-C6MW
- Site as far away as posible from any lighting or ventilation equipment
- Do not install in or on a vibrating surface
- Do not fix to a suspended luminaire
- Site as far away as possible from the surface of metal objects
|Supply Voltage||230V AC ±10%, 50Hz|
|Channel 1 Load||10A fluorescent, low voltage, LED|
|Channel 2 Load||Maximum number of dimming ballasts = 10 (relay enabled)|
Maximum number of dimming ballasts = 20 (relay disabled)
Dimming output is not SELV, Mains rated cabling must be used.
|Power Consumption||On = 1100mW|
Off = 664mW
|Timeout||Adjustable 10 seconds to 99 minutes|
Optional adjustment by remote controls
|Temperature||-10°C to 50°C|
|Humidity||5% to 95% non-condensing|
|Material||Flame retardant ABS and polycarbonate Class 2|
The microwave radiation emitted by these units is extremely low power and complies with ANSI standard "IEEEC95.1-1999. Standard for Safety Levels with Respect to Human Exposure to Radio Frequency Electromagnetic Fields 3kHz 300GHz".
Wiring Diagram 1 : Switch And Dim Together
Switches the luminaire with occupancy detection and maintains illuminance. Dims and switches using the centre biased retractive switch.
Wiring Diagram 2 : Switch And Dim Separately
Switches both channels with occupancy, maintains illuminance, dims and switches the dimming channel using the single position retractive switch 2. Switches the switching channel on and off using the single position switch 1.
Wiring Diagram 3 : Two Channel, Common Switch
Switches both channels with occupancy. Maintains illuminance, dims and switches the dimming channel using the centre biased retractive switch.
Wiring Diagram 4 : Single Switch Only
Switches channel 1 only with occupancy, optional override switch, no dimming output.